I spent the better part of last night messing with a new 3 way leviton dimmer and remote to no avail.
Finally, I think understand what may need to be done, but the box to control the actual dimmer does not have a neutral that connects directly back to the neutral that enters the original circuit. The switch box does have 4 total light switches in it and a separate hot for another switch as well as a bunch of neutrals wired tied in together. Can I just make a small neutral wire and piggy back my switch to the neutrals of the other switches, or will the dimmer not work?
Thanks for any help~ I"ve also added a diagram of what i plan to do.