I have recently moved out of an apartment and into a house and I have been trying to set up the 3 way smart switch(es) that I used at my apartment.
I have a switching remote DD0SR that goes with the wall box with the Line hot connection (according to the instructions) and I have a DDS15 switch for the Load Box connection.
For the box with the line hot, there is a ground/green wire, a white/neutral wire, a black wire (hot), and a red wire.
For the load box, I have a ground/green wire, a white/neutral wire, a black wire, and a red wire. When the box with the line hot is connected to the 1st switch, the load box has a charge in the red wire, but not the black.
The only way I can get the lights to come on is by putting the black and red wires in the same terminals on both the hot box and the load box.
I’ve attached 1 picture that has 4 pictures combined (since new users can only attach 1 image here). Sorry it looks like a mess.
Any guidance is much appreciated.