New user here. I’ve been reading for a while before I took the plunge.
I’m replacing a regular 4-way switch with a smart 4-way switch. That’s 3 switched.
I understand I need neutrals at all 3 locations. unfortunately I only have neutrals at 2 locations. For the 3rd, I tapped into the neutral of a nearby outlet. That outlet is on a different circuit. The switches seem to work. I get voltage when the switches are on and no voltage when the switches are off. However the light does not come on. I’m thinking it should work since I get voltage. Also a neutral is a neutral. They all go to the neutral bus in the panel.
I’m stomped. I’d really appreciate some help or suggestions.