It seems that you are the resident expert in the Mimolite here. Perhaps you can help me. I am trying to use the Mimolite to turn on a vent booster fan, when the hvac fan goes on. Since the HVAC airhandler is controlling fan on/off, I have tapped into the 120vac line, then fed that into a 12vdc converter. This is feeding the Mimolite input. It paired fine and responds to the controller, in terms of manual on/off. Put the input voltage does not trigger an event. Steve at FortrezZ said this:
So, if I understand your situation, you are looking to have our signal input trigger our Relay on MIMOlite? You can do this, see below:
The MIMOlite can be configured to automatically turn the relay on when the input is triggered. The Configuration Command Class, Parameter 3, is used to set this mapping. When this mapping is enabled, Z-WaveTM commands to set a relay are overridden. The default for the relay is no input-to-relay mappings.
Parameter 3, SIG1 to RELAY1 mapping, is enabled by setting Bit 0 in the parameter value field and disabled by clearing the same bit.
Trigger Mapping: Trigger level on SIG1 sets or clears Relay1 or ‘(Refer to description in user manual under section, Input to Relay Mapping). Note that neither a Basic Report nor a Binary Switch Report is given when Relay1 is automatically set or cleared by Trigger Mapping.
This is where I’m lost. I am not a coder. This automation scenario doesn’t seem that odd to me. But I can’t find anyone doing it. Thanks in advance.