I have a new build house that doesn’t seem to have neutral at one of the switch boxes. I mistakenly bought a Leviton HomeKit dimmer thinking I’d have neutral everyone.
I am trying to update a 3-way switch that controls 6 overhead LED can lights. I think I have line-switch-load-switch-1 (how can I tell)
Load/line is at one of of the gangways (neutral is in the back and capped) and there is a 3-way cable that the existing dump switch is connected to that’s red, white, and black. (The white does NOT have black tape)
What I presume is the slave gangway has only one 3-way cable coming in with red, white, and black that’s all connected to the switch (I think common + 2 travelers). There does not seem to be a neutral. I assume without fishing a neutral I need to swap to something like the Castera?
There is no way to re-wire my existing setup to work with the Leviton (which needs 2 travelers, neutral, and load)? Or can I hook one of the travelers to neutral and then use that on the other end of the 3-way to power the remote?