I hooked up my 3 way in my downstairs hallway with zero issues
I am trying to do the one on my stairs right now
My upstairs is the line wallbox, I hooked upp the DW15S like I always have in the past, black hot wire went into the ‘black terminal screw’, my traveler ONE black wire went into the ‘YLRD’ terminal next to it, neutral went into the white/chrome terminal, ground went to the green, and the second traveler wire (red), went into the red terminal
For the downstairs (load)unit I am using the Leviton DD0SR-1Z wall switch (which is the same one I used in my hallway 3 way) is the other one it only had 4 wires a black, red, white, and ground, what is odd is that the downstairs white wire seems to be my ‘hot or load’ which is new to me…
I connected the white and the red (which was traveler 2 upstairs) together along with a wire connector, grounded the device, and put the black wire in the YLRD slot.
My upstairs switch can turn the light on and off, downstairs does absolutely nothing
SO, I tried switching the upstairs traveler terminals, red in the YRLD, and black in the red terminal
I go downstairs and switch the red with black to connect to the white, and light begins to flicker whether or not the switches (up and downstairs) are on the on position.
I believe I have the upstairs hooked up correctly the first time, the black traveler 1 in the YRLD, and the red in the red terminal, because the light turns on using the switch upstairs.
I have tried multiple and I mean multiple combinations for the downstairs, and I cannot for the life of me figure it out.
I am pretty sure I do not have an LED bulb, because it would have most likely flickered with the 3 way switch that was already in the house. Plus I tried several other bulbs
I used this video:
Any tips would be great thanks