Last one I promise! I have a fan/fan light combo that is controlled by 3 switches set in two switch boxes. The first switch box has 1 switch for the fan light, and 1 switch for the fan blades. Across the room there is one more switch for the fan light. I need help wiring the fan light’s two switches to a GE 12722 and GE 12723.
SwitchBox1 has 2 switches: Fan light and Fan Blades. The hot line from the breaker is in this box.
SwitchBox2 has 1 switch, only for the fan light. There is a single romex coming into this box
Fan/light: There is a single romex coming into the junction box above the fan
I apologize for the horrible pictures, it was dark last night when I took them. If it is not clear with these pictures I will take more when I get home today.
I took a single picture of the fan and a single picture of SwitchBox 2 because those are pretty simple. The rest of the pictures are of SwitchBox1.
These pictures were taken at different times, so some of them you will notice I labeled one of the red wires as LOAD. This one I am 99% sure goes to the romex in the junction box of the fan light.
There is a white wire that is tied into the black line wires in SwitchBox1. If I remove that white wire and power on the breaker, all lines in both boxes and at the fan are dead except for the group of black wires that it was tied into, telling me that the group of black wires is the line from the breaker.