So, a couple of months back Navat604 (Ray) and Chris_Crowder helped me get some GE 3-ways switches done and they work great. Since then I have installed a bunch more without any issues. Today, I was hoping to install this new GE dimmer switch to replace a single-pole light switch that happens to be in a 3-switch gang-box. But much to my surprise, when I opened the gangbox, i found no neutral lines like i had for all the other switches I have replaced to date. But this is the first 3-switch gang box I’m attempting.
In the picture above, for now I was only looking to replace the center switch. That center switch is the only switch used to turn on my living room lights. The switches on the left and right have romex cables with 3 wires and a ground. The center switch romex is just 2 wires and the ground. Is there a way around this problem or am I in serious trouble here? Ultimately in time I was hoping to replace all the switch but the switches on the left and right are 3-ways switches and I thought I would hold off on them a little while longer.