I have a strange wiring situation that I am having trouble figuring out. I have a 3 gang box with a single switch for the porch light, a 3 way switch for the hall light and a dimmer for the foyer light. I am trying to change out just the porch light.
The regular “dumb” switch had 1 wire that appeared to be connected to both the line and load and the neutral wire is wired to the neutral on the other switches and then to the neutral bundle in the box. The strange part is when I cut the wire that went to both the load and line, I have power at both.
Any suggestions on why?