I am hoping that someone more electrically inclined can help me. I have a three way hall light that has two light fixtures. I have tried to read up on how to wire this correctly but I haven’t been able to find a similar wiring scenario to what I have.
This is what I believe is the main switch. In this box I saw that a black and white wire are tied together which I think is running to the other switch to supply power.
This is where the add on switch should go but I am unsure of how to wire it since it does not look like I have a neutral. The white wire looks to be acting as the line in power and also looks to be the end of the run since there are no other wires leaving the box.
Any help will be appreciated.