First off I know the first reply will probably be dude call a certified electrician. I completed all my single pole and two switches successfully un my house but my living room 4 way is driving me crazy.
I have the single pole outside light working just fine with proper line and load configuration so there’s no problem there.
I have a single pole fan that I had working with my ge fan switch and I’m sure I can figure that out.
My real question and with the photos below is pertaining to the 4 way livingroom lights that have three switches, and the 4 way light connected to the fan. I wants had them all working but only if the master switch was on so I know there somethings wrong.
Wondering why I have so many traveller wires in this one gang box. My house is brand new and built by an electrician so I hope and think he did every right, I mean everything worked with his toggle switches before I messed with it. Lol