Hi there, I’m trying to install smart dimming switches to my kitchen lighting where there are two switches currently connected 3way. One of the switch box shows a bunch of white wires connected together which are neutrals, but when I opened the second switch box, there wasn’t the same, instead, there are four wires a ground that’s is not even connected to the switch and a black, red and white connected to the switch. Could the white be a neutral? Or would you say there is no neutral in this box?
This is the box that only has one white to the switch.