Has anyone here got experience of the Dimmer 2 installed in 2-wire installations with 3-way (or greater) circuits and toggle switches?
I have put together a test circuit and the switching all works fine manually (single toggles required), and the Dimmer 2s work fine remotely, but I have an unusual behaviour when mixing on and offs between physical and remote.
For reference I’ve used the wiring from the Vesternet site (http://www.vesternet.com/resources/application-notes/apnt-112) but not bridged the Sx and N contacts (as this resulted in a red overload led on the module) and switched the light off after about 1s.
If I switch on physically, then switch off remotely, the next physical switch on will require 2 toggles to turn on. Equally, when I turn on remotely, and then turn off physically, I need another 2 toggles. Even more unusually I’ve noticed that in some states, the final switch in the circuit will work with 1 toggle (i.e. as expected). Can anyone confirm if the behaviour I’m seeing is what should be expected or is it indicative of a wiring anomaly somewhere? If it’s by design it’s a bit disappointing as it prevents me transparently installing into existing circuits - not keen on replacing switches.